This video I installed a 3/4Hp submersible pump at 300ft. Although the video is long, I try to fully explain from start to finish & why I do the things this way. My average life span of the pump I install all 15-18 years on 1/2Hp @ 100ft & 12-15 years on 3/[email protected] 300ft. I do NOT use torque arrestors or plastic centering rings. They can cause issues when they get old or if the well needs camera inspections. Tapping the wire every 3ft to the bottom side of the pipe is key to not having wire chafing issues. If you need Help please comment and I can diagnose any issues on here or the phone. Help is completely free & any donation would be appreciated but not neccessary at all. I will help anyone with absolutely any water issues! Thanks for Watching & I hope it helps!